upgrade from SV 5.0SP2 Rev D to 18.104.22.168
We are planning to upgrade system SV 5.0SP2 Rev D to 22.214.171.124. After connecting controller with new upgraded system, OPC (smiley) is not getting connected. We are getting "files missing " pop up with an option to browse required files from CBM location.
If we try to browse files (copied from 5.0 sp2 Rev D CBM to 126.96.36.199 CBM) required by OPC to get connected, we are getting message pop up "File Path/access error"
Anybody have faced such issue while upgradation ?
Thanks in advance
I faced similar problem in 188.8.131.52. In my case I did download from Control Builder to the controller.
Then I went to OPC Server and enter the IP of the PLC, I wanted to connect (appear with red cross).
The OPC asked me for missing files, and I selected them from Control Builder directories, not from OPC directories.
C:\ABB Industrial IT Data\Engineer IT Data\Control Builder AC 800M... or something.
Finally save the configuration in OPC Server .cfg file (that for autoload).
During update, it happen that OPC Server stop working correctly. I found it is MMS Server broken and re-installed it (repair) manually from 800xA media (exe fail is located somewhere in Connectivity folder). So that fixed a problem with OPC Server