redundant network port B in CP800
How to configure redundant network port B in CP800 ?
Answer this question Follow
Follow the steps mentioned in the CP800 latest firmware manual. To make it simple, connect using serial cable (Tera term) and just remove/update the port A ip and come out. Again change\update the ip address of both the ports together at the same time and come out. Regards, Farooq
Hi, the short answer is you cannot.
Both network port (A/B) on PN800 devices are identical with respect to IP and MAC address, backup CP800 will get IP address N+1. So if you have already configured the CP800 according to 2VAA001586 chapter 10 successfully, you then have configured PN800 port A & B. Br HP
Dear CP800s PN800 Port A & Port B uses PRP Protocol that internally acts a single network interface, so you dont need to worry about the other Port.
In the Redundant Configuration the only point you need to take care is os SW2 POLE 3 that should be ON, this will automatically create Network Redundancy. Please share the CP800 Firmware and your IP Range Also Note that you cant keep your Node address as 0.
Other questions needing answers
Symphony Plus >
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal