IIT800xa HMI Alarm Not Matching With DI Object
If an alarm or event trigger before MB300 Upload, the Event Collector service will fail to look up the object and fall back to create a temporary placeholder object below Lost and Found having the object name + a suffix (MB300 network decade:MB300 node number), e.g. (2:61) for MB300 network 21 controller node 61. Such alarms will have a very short context menu because the object type is not known.
Please read this post I made some days ago.
1. Monitor L&F while engineering (and later...)
2. Perform MB300 Upload if new L&F objects appear
3. Purge L&F
4. Trigger a new alarm or event