smart client 2.2 revD RU2 configuration on 800xA 188.8.131.52
existing system 800xA 184.108.40.206 with AC400 connect & AC800M OPC , Two Redundant server (DOMAIN+ASPECT+CONNECTIVITY combined together) & 4 operator clients.
planning to install smart client 2.2 Rev D RU2 (http) on secondary server only , with smart client server node & smart client data provider node together.
smart client desktop pc connect to 800xa server / smart client server on plant network via cisco firewall.
is this configuration ok. will this have any impact on the existing 800xA system performance . how to handle system extension if any on the primary server.
My recent experience with this is: 2 redundant ASCS servers, 800A 220.127.116.11, 2 operator clients, AC800M.
We have installed SmartClient 2.3 (https) on one of the servers. System extension is executed by both servers.
Don't have a visible impact on the system performance.
SmartClients are working well on clients, directly connected to the client network (inside the system). As you probably know - only visualization, no control.
Still we have a difficulties to run the clients trough the router (from the plant network).
I succeed to run the client remotely only in SC mode trough the router (trends only, because our screens are PG2).
Still there is no success in PG2 mode (SC?feature=SCPG2) trough the router.
It would be interesting to me to see the other comments too