Control Builder Error 9080 800XA: The Slave does not contain any or too much input/output data?
How to fix the subject mentioned error 9080 in ABB 800XA Control Builder, pops up when downloading?
Exact Error words: Error 9080: DCS:HW 1.6 Pos. 1.6: The Slave does not contain any or too much input/output data? CI840 connected at Position 1.6 (IO Modules via Profibus network CI854 / CI840). Not giving any for other same CI840 cards, configured with default settings.
Answer this question Follow
Too many I/O modules connected? From S800 Filedbus communication interface manual: "Due to the PROFIBUS-DPV1 specification it is not possible to always connect 24 I/O modules to one FCI. The reason is that the S800 I/O system includes more data and user parameters than PROFIBUS-DPV1 can handle." Check manual for how determinate max no of modules (specifically AI/AO). BR
Other questions needing answers
AC 800M >
CI85x modules >
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal