Hi mate, I understand from your one of responses that you have successfully implemented communication of CI873 with E300 Relay. I am also about to execute the same configuration in 6.0.3 system Can you please explain about the configuration of CI873 for the same, especially EDS file import part?
Hi Kanag, make sure your E300 hardware file settings in CB must be same as E300 relay settings. Disable all keyings in Eds file hardware which you have imported & make sure the FLA1 & 2 settings (Overload current settings) , operation mode should be netoverload at both the ends . check it.. I hope you have configured the same series of IP 192.168. *.* into our CI873 module & as well as E300 relay. create new Hardware library import the EDS file with default settings and you can customize the selections while importing select only (Full Exclusive owner) if you add all it will limits the interface of number of communication devices (E300) for the project with the calculation of IO Bytes. add the hardware and verify the settings as mentioned above .. Good luck..!!