ACH 580 is not giving output voltage 415V / analog input is 10Vdc through BMS
I am using new ACH 580 drive on HVAC - AHU unit, through BMS Analog input is 10VDC Frequency 50hz but Voltage output is 230V, actually I need to run the motor on full speed 415V
VFD running on 50HZ through BMS but output voltage is not 415V
Drive input voltage - 415Vac
MAXIMUM FREQUENCY - 50HZ
23.11 - DI1
23.12 - 20.00 S
23.13 - 20.00 S
30.13 - 0.00 HZ
30.14 - 50 HZ
Answer this question Follow
how you configured the parameters of group 99 - motor data ?
The operation of the drive depends on how many parameters are set, let's start with those concerning the electric motor
Other questions needing answers
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal