AC500 Modbus RTU bug with Coriolis FCB450
Our team has made the Modbus communication with the Coriolis flow meters and manage to read/write from/to meter (we are using COM_MOD_MAST).
Currently we are facing a bug with Modbus communication. The problem is that when the flow meter lost power then the communication is not getting back automatically after power on. In order to re-establish the communication we need to restart the flow meter from meters menu "Devise Reset" (this is a FCB450).
Do you have any idea why this is happening?
Thank you in advance for your support.
This question has not yet been answered.