I have an energy analyzer QA/S 4.16.1
There is no default meter register for M1M
Should I add this meter manually to the meter management
I'm having one more trouble as if I got the readings in the web how I can make it connect to my OPC?
Does this energy analyzer having Modbus TCP/IP if yes how can I configure it
Thanks in advance
Answer this question Follow
This question has not yet been answered.
Other questions needing answers
DCS in general >
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal