Profibus Communication ET200S
Voted best answer
But the HWD definition files and the configured I/O modules in your AC800M project must match **EXACTLY** to the configuration of the specific ET200 blocks that are installed on the bus. Near enough is NOT good enough. Siemens provide many variations of the GSD files for ET200. Make sure you have the right part no's ( as printed on the IO blocks ) and match these against the GSD files from Siemens.
By looking into the web server CFG data, it seems that GSD file configuration is not matching with the Slave Configuration data. Please have a look into the GSD file configured in the slave device you will get some idea so that u can configure the same on ABB 800xA side.