ARG600 network Configuration
I am having a problem configuring two ARG600 Devices with Static IP Simcards to connect a PLC with SCADA .... unfortunately the user manual is no help at all regarding the configuration is just too basic ...
so What I have is an PLC that uses Modbus TCP ( over the port 502) and SCADA that is going to read the modbus from the controller ...
the sim cards don't connect to the Internet and they can be pinged from the ARG600 "Network Test" option (1st ARG can ping the sim card in the 2ns ARG and vice versa)
but my main issue is that computer connected to the ARG600 , it looks like it's unable to forward its connection from the Ethernet Port to the Mobile Wan and thus it cannot reach the simcard "Mobile Wan network" ...
So my Questions are:
1- is this setup possible , using two ARG600 to link a SCADA with a PLC ?
2- Can I create a VPN with this setup or will i need an ARM600 at the SCADA Side ?
Here are the IP settings, if it helps in anything:
IP address of the ARG600 and Related Devices on LAN
Computer : 22.214.171.124
1st ARG600 : 126.96.36.199
2nd ARG600 : 188.8.131.52
Sim card IPs :
1st Sim : 10.200.50.100
2nd Sim : 10.200.50.101
Hello Everyone ,
first of all thank you for the comments/feedback it helped me alot,
after all of the COVID-19 quarantine periods and delays , I managed to test some of these options but unfortunately to get the ARG600 to work , I ended up needing the ABB ARM600 communication server and create OpenVPN certificates to connect the PLCs through ARG600 to the network through openVPN and then to SCADA which is connected to the ABB communication server...