800xA 6.1 Version, when using IEC61850 Object library, Alarms are coming on one same conducting equipment name
I created 4 conducting equipments in IEC61850 Object library. Each conducting equipment is called in functional structure namely Q01, Q02, Q03, Q04. These 4 conducting equipments are mapped to same IED (RTU in this case) in control structure during SCD upload. I used Decoupled IEC61850 Engineering method for SCD file upload. When there are any alarms of Q01 or Q02 or Q03 object name of Q04 is taken. In 800xA 6.1V IEC61850 manual it is provided that we can use same IED for multiple conducting equipments. Does anyone encountered this problem?
This question has not yet been answered.