Discrepancy between ControlBuilder and ControlStructure
I have a problem with discrepancies between ControlBuilder Hardware Tree and dito in the ControlStructure of 800xA. The order of I/O cards connected to some CI801 slaves are wrong in the 800xA control structure. What's the remedy and correct actions, running Name Upload?
System version 220.127.116.11, connectivity AC800M, CI854 PB Master.
I believe the order in 800xA Plant Explorer is simple Alphabetical ordering. Shown in tree is the .:Name:Name Property, while Control Builder shows the .:Control Builder Name:Name Property - those two may be different and this may be what happened in your case. So can you compare Control Builder Name Aspect with Name Aspect for those items, and try to manually set Name on Name Aspect to the same value as in Control Builder Name to check if this already solves your issue?