Communication Using MODBUS DRIVER in CHMI Version 184.108.40.206
Can some one tell me how to communicate in CHMI( version 6.03.2) Using the Protocol as MODBUS Driver Ver 220.127.116.11. Using MODSCAN 32 bit software ...where i used to find out the address location starting from address...31561,31562...etc..( Below attached screenshot for reference). Using this Adddress i try to communicate in CHMI with Protocol as MOdbus Driver.But communication is not happening. Below i attached Communication Parameter Settings & Modcan Connection settings screen shots as Reference. please someone help me to work out the communication procedure. In case any manuals available please attached the link below.
Thanks in Advance
According to Modscan picture you query Word data type, but you have configured Real Data Type under PLC Connect.
You need to define your type as Integer under PLC Connect.
If you want to use 32bit Float data type, you also need to define your address as HRAxxxx,REAL for floats.
Hope it helps.