Undefined Service in redundant ASCS 152
i work with v.5.0.1 AC800M after several power failure due to our downtime i try to restart our ASCS152 (we have 2 ASCS(ASCS 152&153)) one of them starts with all Green But the other all service enable But Undefined. now downtime is over and system is running how can i fix this without disturbing process thanks in advance.
Answer this question Follow
The resolution on your pics are not good enough to see details... I guess you've tried several restarts? Probably network related, check network cabling, status (RNRP), including logs. Could there be a network device that lost configuration after the power failure (port config/VLAN etc)? BR
I see you have disconnected and non functioning network cards. This can sometimes cause problems with RNRP binding to IP addresses that don't work and prevent your system from starting properly. You should resolve these Network issues or disable network cards that are not required. In any case, unused network cards must NOT use IP addresses that are automatically configured by RNRP.
Other questions needing answers
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal