Hi , I have existing PM582 , AC500 controller which is communicating with DigiVis 500. The communication is not consistent and Customer want to integrate it to existing Freelance 2016. How can we do this.Either modbus TCP/IP or DigiVis are the options.Do we need any additional license either in AC500 or Freelance2016. Existing Automation Builder is old version and may need to upgrade it to latested.Customer don;t have license details. For me this is first time with AC500 product.
AC500 data can be integrated to Freelance 2016 directly without need of DigiVis 500, because Freelance 2016 succeed DigiVis 500 for AC500 PLC. For this you need Freelance 2016 with license (as per your requirement).