PanelBuilder 800 v6 with SoftSontroller
I have problems connecting a simulated panel with SoftController.
Compact Control Builder 6.0.0-1
Panel Builder 800 version 6.1-0
I have set it with SoftController as Station 0 with an IP address 18.104.22.168 .and as Process Id 2.
Connection type set as ABB controller protocaol Control Network for AC 800M.
I can download to SoftController and it is running. I have imported tags to the PanelBuilder via the "Import tags to [ABBMMS]". So the PanelBuilder can see Control Builder.
But when I go Run in PanelBuilder I just get ABBMMS Comm error :0
The other issue is that the screen that shows up in Run is not the whole screen. Why is that? I would expect to see the whole panel with the physical buttons as well. How can this be tested without the panel if this is how it's work?
You must make sure that the IP address of the controller is assigned correctly. To do this, you must access the tag configuration, then on the controller tab, click on configuration and then on the station tab. There you must have the address of your soft controller assigned.
To solve the screen issue, go to project tab and select Configuration, there you must select PC in the destination type box.
I Hope help you