what i need to configure in the PCM600 to communicate by modbus to the PLC?
HI, i want to communicate a REF615 with other REF615 by goose massages but at the same time I need a communication with a PLC (PM573-ETH ) by modbus TCP/IP. the three devices are conected to a switch.
and i would like to know if the communication by IEC61850 affect the modbus comunication. thanks.
Answer this question Follow
Voted best answer
Hi. you need to configure your relays to communicate with multiple OPC servers. You can use IET600 tool for the same.
2nd. I am not sure whether when 2 relay communicating with each other on Goose can responds to 3rd master on TCP/IP. Can you please share the configuration drawing for more information.
Hi, first of all thanks to the answer. Just i need to read a register from the REF615 to the PLC to send by a analog output that signal (but i need to do this while the IEC61850 is betwen both ref615). i read in the modbus comunication protocol manual that is possible communicate by two protocols simultanusly. but i do not know if both protocols works in the same port and first work one protocol an then works the other second. and i don't know what i need to configure in the ref615 to active modbus protocol.
Other questions needing answers
Distribution Automation >
Feeder protection & control >
PLC Automation >
Processor modules >
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal