ow to convert DintIO to RealIO value in Control builder M Professional Version 5.1
U can see the above value is in DintIo. We want to convert the value in Realio value? What is the procedure?
Voted best answer
- Your Hardware definition file is wrong. Fix it and use a RealIO datatype, not DIntIO
- You cant just convert DInt to Real, because the Hardware definition is wrong. The DInt datatype does not contain a Double Integer, it contains an IEEE floating point number. The DInt datatype cannot present this properly.