AC800M communication with Conzerve meters on Modbus
Answer this question Follow
Voted best answer
Please check the start address format. Also you have to give 1 register less value to read the parameter. for example- frequency is in register 3110 (32bit data), then in control builder you have to read 3109 register.
Other questions needing answers
AC 800M >
CI86x modules >
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal