Hi all. I created new DS database by online builder .. but valid=0 & error =1. Do we need to warm start controller to clear the issue.. or we have another way ?. The sender side is ready ( valid =1)... but receiver side is not ready.
From my experience, after CRDB DS in Online builder you must go to Configurational mode by ECONFIG to initialize new DS and then go back to Operational mode by DICONFIG. Check if there is any spare DS either with ACT=0 or 1 or if it is possible to extend any operational DS.