Getting rid of "System condition events" with bad quality. 800xA 6.0.3-0
System version 6.0.3-0
I have several alarms from I/O-channels with the "Quality:Bad, comm failure". Is there any way of flushing them out? Following have been tried without success: 1. Stopping "System message server" on both aspect servers and then renaming the actual folder in "C:\OperateITdata\SystemMessage\FolderName_OLD". 2. Same procedure as above but for the "Soft Alarms" service.
Answer this question Follow
Voted best answer
Alarms of category "System Condition Event" are emitted from AC 800M hardware and cannot be suppressed in the HMI (I am not counting the possibility to place an attribute filter to "hide" them as a way forward).
Check your settings in Control Builder M (maybe you can suppress them from the controller end). If not, you need to disable the unused I/O channels causing the underflow.
Other questions needing answers
Alarm & events >
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal