When aspect server is down or removed primary client server network, getting other nodes alarms as prim or sec nw
When aspect server is down or removed primary client server network, getting other nodes alarms as primary or secondary network failed. These alarms are coming from node admin structure. As a soft alarms.
This system is in domain and system version 6.0. Rnrp showing proper status. Kindly let me know how to fix this issue.
Answer this question Follow
Please file a support case with your regional ABB Support Center.
The ”Network Connection ...” alarms are calculated by the System Status service with input from the local RNRP service and exposed via SoftAlarm. At failure of the first System Status service provider (AS1) the secondary (AS2) should take over and provide the network connection view from its own RNRP status. AS2 should see more or less the same network and node/path status as AS1 did before going down. When reporting this problem, attach the C:\ProgramData\RnrpEvent.log files from the affected servers and some clients for comparison.
Other questions needing answers
Aspect system >
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal