This is Peyman A. Baghaei calling you from ABESTA co., in Tehran, Iran.
We are active in the field of industrial automation and support some of the most reliable plants in Hydro & thermal Power and petrochemical plants technically.
I have a technical problem and trying to find someone, I found you contact info in Linkedin.
Recently, we have supplied two ABB AC450 PM511V08 modules for one of our client in Hydro division as spare parts, modules are from china, and they seem new.
When we put the module in sub rack and initializing it by turning power on, the power Led turns on but after a few minutes, instead of entering initializing state P1 or P2 or … like that, the red fault LED on the module turns on and the module is inapplicable. Moreover, we cannot connect the module via the ENG station in control room.
Would you please determine where the problem comes from?
Is it because of firmware mismatch ?
Peyman A. Baghaei
No. 26, Ashrafi blv., Tehran, Iran
Tel: +98 21 44891147
Whatsapp: +98 910 169 2171
You can only connect the engineering station to the CPU when it has booted into P2 or P1 mode or crash stopped in P4 mode.
Based on your query, need some to information if possible you share pic to my email id Chidambara.deshpande@in,abb,com or you send me message through linkedin
1. How did you started when you replaced with PM 511 (CPU) ?
2. What version of Flash card library ??
3. When you restarted the PM 511 (CPU) where was xxxx position ( should be in position 3)
4. When you powered on what was the indication on the CPU ??