Add new comment
Need the status variable bit in control builder to use it in logic.document attached shows only the status to be shown in graphics.
Without PNSM, Node NICs status is not possible to be read in CBM. Refer below answer.
The attached document is for checking node's status (bit change if both LANs of the node are down). It is not only for the graphics, but includes Property Transfer to move the variable from Graphics (PPA) to CBM.