Advacommand 1.9/0 and Advabuild 2.9/1 Patch ABB-PSSU 146072 eDCN OSES Station
Good morning , please could you support in the following?
we have installed the patch ABB-PSSU 146072 eDCN onto OSES , to try to fix the eDCN issue regarding to the Synchronization , and we have followed all the step writen in the release notes document , when we did the procedure regarding to D2E , from bugs it spent a lot of time and it showed TIME OUT , but it showed D2E.PK and D2E.OL under FMS[50.D2E] , we followed the procedure according to the release notes , after finishing we pulled CS513 out and SC540 then we put back CS513 into SC540 , then we put the SC540 into the card file properly , but the SC540 did not boot from
According to the information there is another patch ABB-PSSU 146086 for this eDCN issue and it can be installed from 14.6 version or later , this system is 14.6/4 , then we could also try with it .
Do you have any another idea?
Thanks for your support
, it kept down ( red led ).
1) The release notes tend to be particular about timings on removing and replacing cards. So if you wait to long, the card can fault.
2) My advise is not to install a patch developed for a newer version onto your system.
3) Having entered the world of eDCN this year, we've struggled at times. We attempted to use modern Cisco switches but they could not handle the proprietary eDCN packets. In the end we ordered the new ABB switch (NE840) and configured the ports for 10MB, 1/2 duplex.
Also I would be conscious of using shielded cable in place of standard network cable.