i am able to browse tags in matrikon, but not able to connect to 3rd party opc server in plc connect .
I have installed matrikon and 800xa plc connect in the same system of 800xa (say abc system). i am able to browse tags in matrikon. we configured plc connect as follows;- installed plc connect softwares and the graphics for it;- created plc connect object in plant explorer;- in configuration of plc generic (given this system(abc system));- create d new object in the controller of this plc client object;- in the scroll down given plcclient then in edit drive given 3rd party opc server ip address, but it is showing unable to communicate to opc enum, but in matrikon it works fine, please tell us a solution
Make sure you have configured the DCOM settings at both the ends (PLC Connect server node and 3rd party node); as Matricon will bypass the DCOM, but PLC Connect won't. If possible, share PLC Connect log files from path: C:\OperateITDataXXX\AdsServer.