IEC 870-5-103 with AC900F
I am new in this blog, and i am looking for answers, hoping someone can help me. I would like to know how to communicate a Protection Relay RE670 (by ABB) protocol IEC 870-5-103 with a AC900F. Is there any suggestion? BR
Answer this question Follow
Voted best answer
AC 900F does not support IEC 60870-5-103, only ...-101 and ....-104. A solution would be to use a Modbus TCP to IEC 60870-5-103 converter like for example the 5201-MNET-!03 Gatweway from Prolink. See Source link below
Other questions needing answers
AC 900F >
Application Knowledge Store (AKS) will no longer be available after the 31 July 2021.
We are enhancing our Customer and Partner experience and will be migrating data from AKS to the new portal.
During the transition please direct your questions to:
If you are an ABB customer with a CARE Agreement you can access our Customer Portal, where you can find solutions and ask questions, and communicate directly with ABB.
If you are not an existing CARE customer with ABB please contact your local ABB sales office.
For our authorised Partners you can directly access additional support information in the Partner Portal