How to make Infi90 BRC controller accept the time of the Harmony Connectivity Server? 800xA time sync with BRC410
This should solve your problems. Please note: if there are 3rd party software connected to the same loop (eg Historians) they can also drive the loop time in-advertantly and these will have to be dealt with separately (it takes too long to explain here).
PS to determine Timesync on 800xA for Harmony:
Use the Server Diagnostic to determine the Infi90 Time Sync Master by using the following procedure:
Start the Web base Server Explorer
Right click on the Harmony-Server for the node and select the Server Diagnostics
From the General tab scroll down to the Atoms named TS/MSTR_LOOP_ACC, TS/MSTR_LOOP, and TS/MSTR_NODE. These atoms will show the current loop, node number, and accuracy of the Infi90 Time Sync master.