We are preparing a demo system for AC800HI Safety for demonstration to custuomer.
As part of this we want demonstarte the SOE functionality of DI880 modules.
Request to share the procedure if any for the same.
This could be one of the possible ways-
You may connect a DI channel to "event detector" block thru a variable and set ExtTimeStamp parameter to true to read time stamp at module.
Connect the same variable to alarmcond block. Use a slower application interval time for the application. you shall see two events with different time stamps.