Object naming works bad in 800xA - 61850 integration
I have a redundant 800xA 6.0.3 system connecting 17 Micom terminals. All the terminals are equally configured and the IET configuration seems to be ok. I get all the alarms and events in to 800xA but for some terminals 800xA reports the 61850 property-name as object name and for some terminals the object name is correct according to the configuration in IET. I have reviewed the configuration but can't see any difference between the terminals that works ok and those delivering stupid object names. I use the standard lib for the uploader and have avoided all unnecessary configuration stuff I can.. Has someone seen a similar behavior? It doesn’t help to delete all uploader generated objects in 800xA and regenerate it all. The problem is still there...
Sounds familiar - please file a support case.
IEC61850 is in total control of matching since it send A&E with a SourceGUID attached. The SourceGUID will be translated into object name by 800xA. For this to work; IEC61850 and HMI must agree on GUID. HMI is master. 61850 need to be downloaded with correct settings.