Ability of PU410 to connect to "ABB Master" old CPU : DSPC 172
Can the "PU410 Engineering Board" support the old "ABB Master" "DSPC172" CPU?
Can I read CPU's logic and change it by PU410 connected to our installed Control Builder A 1.3 software?
I know that the port PC1 (Ethernet) should be connected to the PC (Server Connectivity or Engineering Station) but which port of PU410 should be connected to the ABB Master system?
It's clear that the Ethernet should be connected to the PC, but the RJ-45 cable should be connected from where to where?!
"From" MB300 or CBA port?
"To" the MasterAid 220 or MasterView230?
I attached our MasterAid 220 ports for better help.
Thanks alot for your help and answering to all questions.
The PU410 has two Ethernet ports, two MB300 ports and one serial port.
Advant and Master controllers can be programmed via serial or MB300 connection.
To program via serial connection, connect CBA PC via one of the Ethernet ports and the controller via the serial port.
The most recent CBA version is 1.4/0 compatible with Win7/8/2008R2/2012.