Hart configuration issue
I am doing hart configuration and ensure that asset optimisation service is running and the FBB OPC source definition is configured but it wont come to service state and stays in initialise
we have imported the structure from one system and imported to this system and have ensured the system extensions also
I am unable to find the hart channels under AI815
please find the snaps for the info and suggest me
FBB OPC will remain intialized untill you do OPC server configuration successfully.
However your configuration seems to be odd. The icon of HART devices does not look like you attached in picture.
Also Fieldbus management aspect is empty which shows something went wrong during import.
Can you create a new Generic HART transmitter under AI815 and attach results?
Provide details to understand better.
From Which version of system you have imported? Is it both systems are running with the same system version?
Have you stopped the communication before importing the aspect-objects?
Is it tool routing is running in the new system?
If not enable & download the controller.
Is it Hart objects are loaded in the new system via library device manager?