Im Creating a new Project in Control Builder & Connecting a Controller.
As of my knowledge, Controller takes time from Server. But Please see the attachment. Why there is a deviation?
The Alarms generated are showing correct time. But in this block(image file), time is wrong. Even in help file of CB, it is mentioned controller takes time from System/Local time can also be set
Voted best answer
I hope that your controller settings are properly done to receive time from Connectivity Server - SNTP
Please verify CS Protocol type,CS Time set enabled and CS SNTP Server Address(in your case it will be CS IP address) -
Check your Clock Sync status(add your controller node)
Let me know if this does not solve your problem
The informtion that you have provided is insufficient. The controller doesnt take time from the server by default. You need to specify the time source for the controller to do so. At the same time you need to disable the time adapator in the Connctivity servers.
I recommend you to refer 3BSE034463-510 E-System 800xA Network Configuration , section 7 page 145 onwards for time sncronization. If you need further help please contact the local support organization.