How to create redundant configuration
I want to know how to create a redundant configuration with CI868 module in IEC 61850 protocol.?
You need check the "Enable Redundant Mode" and select a position for backup unit while inserting the CI868 module from the the Project in the control builder
The Path is Controllers ->Controller -> Hardware AC800M --> AC800M controller -->CI868
Unfortunately we don't have module redundancy for CI868 in AC800M available yet. We have only "application redundancy". This means that you must have 2 CI boards in the SCD file receiving the same GOOSE messages. Then your application must select which variable to read, based on the ".q" attribute.
You can see more info on the attached manual, page 127.
Please let me know if this explanation was enough for you.