PM564-eth and dx522
I have a problem with connecting pm564-eth and pc with ethernet.
When I get into the Control Builder Plus and adjust and optimize pm564-eth and dx522 with control builder, I open AC500 and next resources, PLC Configuration I didn't found a settings of PM564 and DX522. potential problems how to solve it?
1. For configuring the Ip adress you have to use IP configuration tool, found under tools in control builder+ v2.2.
I have attached a dokument with how to do IP configuration with AC500. Use page 5 to 7.
2. Define the the communication parameters in Codesys under online-->communication parameters.
Make a name
Set in the right adress
Check Port 1201 and Motorola byte order Yes.
Then you should be able to connect.
Do not use the Force ip settings you find under Ethernet-->PM5x...-->Ip settings.
If you use this setting it will be very hard to change the Ip adress. The best way to remove the ip if this setting is used is to do a reset to original in codesys.