PLC control builder close
When I try to open programm from application of control builder V4.1, control builder gone/close. I already reinstall whole package for 3 times.But I can't restore full Windows due to other software.
please help me
Please contact your regional ABB support center.
The C:\ABB Industrial IT Data\Engineer IT\Control Builder M\LogFiles folder may contain clues to what causes the malfunction.
Compact (CCB) or full (CBM) Control Builder?
I recollect the following reasons (but there are certainly additional ones):
1. CCB/CBM - Corrupt control project. Try restoring a known good backup of the project.
2. CBM - NLS problems (eg from multilingual engineering) may cause trouble. Search ABB Library for bulletins and NLS cleanup tools.
3. CBM - Consistency problems. Add & use Consistency Check aspect to examine/repair the project.