Connect the plc type ( ABB PM554-T-ETH) to pc
hi every one here,
1-how to make connection between PC and plc type PM554-T-ETH , because i have trying to make connection between plc and PC via software called control builder plus and I already used ethernet cable, but the connection was failed, then I have trying to make the connection by used com1( serial cable ) but the plc suddenly power off when I plugged this cable.. how to make perfect connection by steps please to make modification on it .
2- how to rest all error which appear on the same plc
the tool to develope programs with ABB PLC - AC500 series - is Automation Builder, the basic version is free and downloadable in ABB site.
To connet one cpu to the PC with Automation Builder you need to observe the rules of the AC500 device: in case of ETH connection, make sure to have the same domain in your network and in PLC, then you must assign one IP adress of the cpu and use the correct parameter in Automation Builder.
If you use serial connection, you need TK503 cable.
To reset the PLC error you have in Automation Builder the option to read and reset the error, but if you not have the original SW of the PLC, you can not edit it.
More similar questions are inside the forum, for example at the follow adress
Hope this help you