REF615 relay time adjustment
I can communicate with Ref615 relay and I use 800xA.I read lots of data,like breaker position,open position,closed position and time.But alarms time from the relay and scada's time are not the same.What do I do the synchronous the time..
Voted best answer
REF615 supports SNTP,Modbus snd few protocol for time synchronization. You can refer the below document about this time sync. I am not worked on it but i found it from our office site.
Thanks and Regards
the answer for this question is very simple. you have to do the time synchronization for your relay.
on your relay LHMI go to Configuration,inside it Time, inside it System Time, then Local Time offset. set this time as per your GMT in mins, save these settings. then go to time synchronization in configurations then put ip address of your sntp server and save the changes.
it should work.