System Stopped and unabel to start server
It is a standalone system with xA 5.1-0-2 with Compact HMI..When a power failure happened, after restart the system is in disabled condition..Tried Maintanence Stop and Restarted, also by manually trying to start Server in Configuration wizard but to no use.
I have attached log files of COnfig Wizard..Kindly give some suggestion?
Voted best answer
If you see the ABBServiceManager.exe process, but not AfwADServer.exe the \OperateITData\ServiceManager\SMData.dat may be corrupted.
Try compressing it with the Send To Compressed Folder feature of Windows (or WinZIP), if it becomes less than 500 bytes, it is likely corrupt.
You must then restore that particular file from a drive image backup taken from the same computer, or restore a complete disk image backup, or restore a Full Backup of Process Portal A.
Verify that network settings are same after power outage, in some cases the system won’t come up if IP address or computer name is different. The hosts file can also cause trouble if it contain wrong info.