Difference Report Error " Unable to Analyze (Invalid Data) "
Control Builder M is not presenting the difference report , its shows "Unable to Analyze (Invalid Data) " Against the application in the differcence report have attached the screen dump for reference.
Tried Generating Source code report from control builder there are no erros .
But the the source code report generated from the remote system / controller has the same error "Unable to Analyze (Invalid Data) ".
Have any faced this problem or have an idea of what this might be or any solutions or work around.
There are a few reasons this can happen ...
1. You are download the controller from a different Engineering station that the one used for the previous download. - In this case, use the same PC used for the previous donload.
2. This is the first download after enabling difference reports. - Download the code anyway.
3. Something went wrong during the previous download and the controller wasnt properly loaded. Eg Control Builder crashed. - Download the code anyway. In this case you may need to restart the controller.