My system have 2 aspect server and 1 RTA300 borad. How can connect it redundant?
I wantto connect the same network but different PC 1 board it is possibe?
800xa system have Advant Master. System connected the AC410 and upload the 800xa. System show the alarms but I dont Ack. how can control the alarms?
You need two RTA boards or PU410 when you want to make it redundant.
For you other problem you need to load the logical file 25 from the previous system e.g. from the Unix operator station in to the rta board.
Use the following command in the online builder on the os to dump the file
On 800xA go to the control structure and open the RTA board coniguration window and start the online builder from there.
Copy LF25.ld to C:\PROGRAM FILES\ABB Industrial It\Operate It\AC 400 Connect\Advantbase\data\RTA\nodes\RTA\SRCE (the exact location can be a little different between 800xA and or Windows versions use windows search and search for SRCE to find it)
Give the following commands on the 800xA RTA board online builder to load LF25.
SYSTEM NOT IN CONFIGURATION MODE. CONTINUE? : Y
Mode : I*
Finisch with TSESS to close online builder, make an RTA board backup with the RTA board configuration window. Now the alarms should work as aspected.
> "I wantto connect the same network but different PC 1 board it is possibe?"
> "800xa system have Advant Master. System connected the AC410 and upload the 800xa. System show the alarms but I dont Ack. how can control the alarms?"
You need to be an operator to acknowledge alarms in 800xA. System admins and engineers are not part of the operator group by default.