how to reset time sync error in controller
after working on a control network one of the AC800m controllers is giving a time sync error.
While checking the clock sync status all seems correct.
We tried download (warm, cold and init) but only after an init on the controller the message is gone.
To me this seems to be a hickup, or am I doing something wrong?
We are using controlbuilder 5.1.1-2 and in the controllers firmwareversion 5.1.1200.6
Are you using MMS, SNTP or CNCP?
MMS is old and the least attractive choice.
CNCP need a running RNRP protocol.
SNTP need the server to be "authorative" (have good quality time)
MB300 (with CI855) need a running clock master in the MB300 network
Please share the configuration/setup and the error message you got before init.