RNRP Issue in RNRP Versions prior 3.18
Hello Mr. Strömqvist
I´ve read your Answer below this Article.
Are you able to tell me the Knowledge Base Article Number where i can find the information about the following:
"- In versions prior RNRP 3.18 *entire* networks (=path) could be incorrectly reported "down" and in the next few seconds "up" again. If you see cyclical "netw up/down" in RNRP monitor/log, you may be affected by this problem. Contact regional ABB to receive a patch."
We have this defect pattern on one Site.
Voted best answer
If you search ABB Library for "rnrp network down" the first hit should be:
This link should work if you have access to ABB Library:
Access to these documents require an account, but I have inserted an image below
The problem is corrected in the following versions:
ABB 800xA Base 5.1.0-2 (5.1 RevB)
ABB 800xA Base S-FP 5.1.3 (5.1 FP3)
There is also a TC with a corrected version of RNRP, 3.18 which can be sent on request to ABB Support (an active Sentinel agreement might be required).