How to connect GE HPCI IO network which is on Ethernet in ABB system?
EBI001 in ethernet network with GE Fanuc Versamax. How to connect this network in ABB PEC controller?
As I said before, you need to clear on exactly what type of interface module the Versamax IO system is using ...
IC200EBI001 - Uses "Ethernet" - Modbus/TCP. If this is the part number the customer already has installed then you should be able use the CI867 Modbus TCP Interface card with an AC800M.
Versamax IO also supports Profibus, Genius and DeviceNet protocols.
( To explain why I am giving you a "complicated answer" ... when you ask about "ethernet", there are several different - and incompatible - message protocols that can use "ethernet" hardware. It is important to be clear which communication protocol you need to use on top of the ethernet hardware.
For example Devicenet, Modbus/TCP, Profinet, Ethernet/IP and MasterBus300 can all use ethernet cables and switches but are completely different protocols )