is it possible to replace CI830 with CI801
Voted best answer
Yes, but there is a catch. The power supply connection is different, it doesn't have the power supervision contacts. If you replace it in Control Builder M you loose the io configuration, so copy paste that information in an excel sheet, so you can get that back without to much trouble.
Make a backup before you start!