the trend in digvis does not record the status of instruments after i make change object to TSRV,PS01,OS01?
after i make some modification i make cahnge object to TSRV , PS01 , OS01 , OS02 , OS03 then i open DigVis i dont find the curentlly records of trend but the past records still remain after that no records ...... how can i return the currentlly records? thnx
Which modicifations have you done? For example if you've changed the system time or controller time, you don't able to see trends in exact time ranges.
If it is true,regarding this purpose there are same topics here.Please see below links:
If they don't work for you please ping back us again.
Can you please share project tree image in commissioning mode ? because in attached image from configuration mode, it shows OS1 - OS4 is not downloaded and something deleted on OS4.
So make sure changes are downloaded and there is no arrow mark @ digivis resources and digivis resources are in 'Running' status. Also check after user makes load change object to digivis stations from CBF - Engineering station. on digivis station some popup window appears saying configuration changing you need to say ok to that. and then digivis refreshes and run with new changes. try to minimise digivis window if you can not find that popup and may be hiding something in background if there is access to OS enabled.
Hope this helps pls reply back if unresolved.