"X" Symbol on AC500 in controlbuilder Plus V2.3.0
I face a problem related to ABB control builder Plus V2.3.0.After the installation of codesys V2.3 and then after installation of ABB control builder Plus V2.3.0 when i open my project file then i found a "X" symbol on AC500.
Due to this problem i can't open the codesys programme file.On the time of installation i have install "TargetSupportPackage" but still the problem is same.
Voted best answer
As far as I know, with CB V2.3, codesys installs automatically during installation of Control builder.
As per your screenshot, it looks like the Control builder has no reference to the hardware description library in the device repository path or the project was developed in a newer version of Control builder/Automation builder, than that used to open the PLC project file.
I would suggest the following,
1) Try to create a new PLC project by selecting PM582.If you are able to create a new PLC project in control builder, then I suspect issue with version mismatch
2) Check whether the device repository folder contains the device description files
3) Try opening the project in any newer version of Automation builder (Keep a backup before opening in AB)
4) If possible, uninstall Codesys and Control builder and then re-install CB V2.3 (Codesys gets installed as part of the Control builder installation)