Error During gateway connection in Automation Builder 1.2
When connecting plc with automation builder >>>>Codesys>Login>Communication>NewGateway>Tcp/Ip
that time No Gateway found... pop-up comming.
how to resolve the issue.
please find the attachment.
In the attached image, I do not see any drivers configured for creating a communication channel with the PLC.
Click on New Tab>>Select Tcp/Ip driver>>Provide a name for the driver instance.
You will end up with a similar configuration as shown below,
Ensure that the PLC can be pinged via. the same IP as defined in the driver configuration and then download the Codesys program.
Note:When the driver is configured for the first time, the channel info is known only within the AB project.Once a download to the PLC is performed, the channel info gets registered with the codesys gateway and will appear directly as a subtree below 'localhost via Tcp/Ip'.