I am facing an issue that ac450 online builder is directing connecting to the connectivity server node not connecting to the controller node.
In ES computer, through Application Builder trying to the connect the controller, online builder by default it is connecting to the CS server Nodes,
here in our plant we have 3 AS and 3 CS
What is your configuration?
- Local Engineering Board?
- Remote Engineering Boad?
- PU410, PU515A, PU516A?
- Control Builder A version 1.2, 1.3, 1.4 ?
In all circumstances, EBSetup is the central tool used to select local or remote board. The "Test Server" button can be used to ensure proper connection.
Remote RTA/PU410 need proper DCOM settings.
When sharing RTA/PU510 with AC400 Connect, correct installation of Control Builder A on top of AC 400 Connect is required, be sure to answer correct (=yes) when OnLine Builder ask if the installation shall be shared with AC400 Connectivity.
More information in:
CBA 1.4/1 Installation User's Guide, 3BSE066174R201
CBA 1.4/1 Release Notes, 3BSE080911D201